Highly accurate, long term stable humidity and temperature room sensor for residential and commercial HVAC.
The very stylish EE10 enclosure is available in European and US size and in several colours. The snap-on concept allows for easy installation. The active part of the device can be replaced within seconds without any tools.
The measured data is available on two 4 - 20mA or 0 - 10V outputs, on the Modbus RTU or the BACnet interface, as well as on the optional display. Additionally, EE10 features a passive temperature output.
- High accuracy and long term stability
- Elegant design
- Easy installation and service
- Analogue, Modbus RTU or BACnet output
- Passive temperature output
0...95% RHMeasuring range
-5...55 °C (23...131 °F)
±0.25 °C (±0.45 °F)
0-10 V, 4-20 mA, Modbus RTU, BACnetOutputs
24 V AC/DCSupply
Send us your e-mail, we will do our best to help you!
EE10 Datasheet(502.73 kb)
Scaling of the outputs(252.78 kb)
Room Temperature Sensor
Analog, Modbus, BACnet or passive output in an elegant, easy to install enclosure. Ideal for residential and commercial building automation.
CO2, temperature and humidity room transmitter
Dual wavelength NDIR CO2 measurement principle with outstanding temperature compensation and long term stability. High end E+E capacitive humidity sensor. Elegant snap-on enclosure with optional display, BACnet, Modbus or analogue outputs, optional passive T sensor.
What is the difference between Modbus RTU and Modbus TCP/IP?
The main difference is the hardware interface. The Modbus RTU protocol runs on RS485 Hardware while Modbus TCP/IP protocol on Ethernet hardware.
What is the difference between a 2 wire and a 3 wire current output?
Transmitter with "two-wires" technology receive the power from the process, and the signal is carry on return wire (closed current loop). With technology "three-wires" the power supply is separate from current output: 2 wires are the power supply and third carry the signal.