The probe has both analogue and digital outputs and is available with either cable or M12 connector. It is possible to choose between active and passive temperature measurement.
The probe is easily installed and dismounted thanks to the M12 thread. Low power consumption and short start-up time make the EE08 ideal for battery operated systems.
For meteorology and other outdoor applications, the EE08 can be used with the optional radiation shield.
With an optional confugration kit, it is possible to adjust the humidity and temperature reading and set up the analogue outputs.
-40...80 °C (-40...176 °F)
±0.2 °C (±0.36 °F)
analogue and E2 digital (2-wire)Outputs
4.5-15V or 7-30V DCSupply
EE08 Datasheet(843.05 kb)
EE-PCA Product Configuration Adapter(790.77 kb)
Scaling of the outputs(252.78 kb)
Humidity Calibration-Kit Datasheet(642.96 kb)
EE08 Manual(468.02 kb)
E08 Manual Radiation Shield(160.17 kb)
Calibration Kit - User Guide(537.45 kb)
Cleaning Instructions(891.89 kb)
E2 Interface for humidity probes/modules(569.13 kb)
E2 Interface - specification(223.84 kb)
Utilising the E2 Interface(663.63 kb)
EE-PCS Product Configuration Software(21982.92 kb)
EE08 BIM - Building Information Modeling (ifc)(24.17 kb)
|EU Declaration of Conformity|
EE08 CE-DoC(82.21 kb)
Declaration of Conformity to EU REACH(366.08 kb)
Filter: stainless steel wire mesh
Pores size: 30 µm
Length: 25mm (1")
For low mechanical stress
Low pollution level
For high RH / condensing environment
T range: -40...120°C (-40...248°F)
Response time t10/90: 15s
The maximum cable length depends on the product, clock speed and pull-up resistor, and can be up to 10m. For detail please see E2 interface for humidity probes/modules.
Only one E+E device can be connected to the E2 interface of a controller.
Transmitter with "two-wires" technology receive the power from the process, and the signal is carry on return wire (closed current loop). With technology "three-wires" the power supply is separate from current output: 2 wires are the power supply and third carry the signal.